"""
C-6111 ① 생산 정상상태 맵 (플랜 §16.3-5).

PROD 구간에서:
 1) 밸브특성: OP(TICA-6111A.OP) ↔ 스팀유량(FIQ-6115) — stiction/비선형/게인
 2) 정상상태 세그먼트 추출
 3) 회귀: 스팀유량 = f(피드, 리플럭스, 제품, 진공, ΔT…) + 피처중요도 + 시간분할 검증
    → "오퍼레이터 스팀이 가용변수로 얼마나 설명되나" (FIT/MAE)

선행: c6111_extract.py 가 만든 c6111_data.pkl (mode 컬럼 포함).
"""
import numpy as np
import pandas as pd
import matplotlib
matplotlib.use("Agg")
import matplotlib.pyplot as plt
from sklearn.linear_model import LinearRegression
from sklearn.ensemble import GradientBoostingRegressor
from sklearn.preprocessing import StandardScaler
from sklearn.metrics import r2_score, mean_absolute_error

BASE = "/home/windpacer/projects/hc900_ax/scripts/analysis/"
TARGET = "steam_flow"           # FIQ-6115 (에너지). 비교용으로 steam_op도 출력
# 깨끗한 인과입력만 (reflux/dp/dT는 스팀의 결과·동시조작 → 순환참조라 제외)
FEATURES = ["feed", "product", "vacuum", "feed_preheat", "T_C", "T_D"]
OP_RESAMPLE = "6h"              # 운전점 집계 (정상상태 내부 변동 적음 → 캠페인/로드레벨 단위 학습)


def load():
    df = pd.read_pickle(BASE + "c6111_data.pkl")
    df = df[df["mode"] == "PROD"].copy()
    # 엔지니어링 피처: 온도 구배(분리도)
    df["dT_AC"] = df["reb_temp"] - df["T_C"]
    df["dT_CD"] = df["T_C"] - df["T_D"]
    # 기본 정합성: 유량/유효범위 (센서 음수노이즈·결측 제거)
    df = df[(df["feed"] > 50) & (df["steam_flow"] > 10) & (df["steam_op"] > 1)
            & df[FEATURES + [TARGET, "steam_op"]].notna().all(axis=1)]
    return df.sort_values("dtat").reset_index(drop=True)


def valve_char(df):
    """OP(밸브%) ↔ 스팀유량(FIQ-6115) 특성."""
    op, fl = df["steam_op"].values, df["steam_flow"].values
    # 선형게인
    a = np.polyfit(op, fl, 1)
    # 상승/하강 방향별(히스테리시스 ~ stiction 신호): OP 변화방향으로 분리
    dop = np.diff(df["steam_op"].values, prepend=df["steam_op"].values[0])
    up, dn = dop > 0.05, dop < -0.05
    # OP 빈(bin)별 유량 평균 — 같은 OP에서 상승/하강 유량차 = 히스테리시스
    bins = np.arange(np.floor(op.min()), np.ceil(op.max()) + 1, 1.0)
    rows = []
    for lo, hi in zip(bins[:-1], bins[1:]):
        m = (op >= lo) & (op < hi)
        if m.sum() < 20:
            continue
        fu = fl[m & up].mean() if (m & up).sum() > 5 else np.nan
        fd = fl[m & dn].mean() if (m & dn).sum() > 5 else np.nan
        rows.append((lo + .5, fl[m].mean(), fu, fd, m.sum()))
    hb = pd.DataFrame(rows, columns=["op", "flow", "flow_up", "flow_dn", "n"])
    hyst = (hb["flow_dn"] - hb["flow_up"]).abs().mean()
    print(f"[밸브] 선형 flow ≈ {a[0]:.1f}·OP + {a[1]:.1f}  "
          f"(OP {op.min():.0f}~{op.max():.0f}%, flow {fl.min():.0f}~{fl.max():.0f})")
    print(f"[밸브] 상승/하강 평균 유량차(히스테리시스≈stiction) = {hyst:.1f} "
          f"(유량 스팬의 {100*hyst/(fl.max()-fl.min()):.1f}%)")
    return hb, a


def regress(df):
    from sklearn.model_selection import train_test_split
    # 운전점 집계: 정상상태 내부 변동이 거의 없어(98% steady) 점단위 학습 불가.
    # 6h 중앙값 = 캠페인/로드레벨 단위 운전점 → 진짜 f(부하) 신호.
    ops = (df.set_index("dtat").resample(OP_RESAMPLE).median(numeric_only=True)
           .dropna(subset=[TARGET, "feed"]))
    ops = ops[ops["feed"] > 50]
    print(f"\n[운전점] PROD {len(df)}행 → {OP_RESAMPLE} 운전점 {len(ops)}개")
    X, y = ops[FEATURES].values, ops[TARGET].values
    Xtr, Xte, ytr, yte = train_test_split(X, y, test_size=.3, random_state=0)

    # 베이스라인: 피드만 (steam/feed 비율제어가 얼마나 설명?)
    lb = LinearRegression().fit(Xtr[:, :1], ytr)
    r2_feed = r2_score(yte, lb.predict(Xte[:, :1]))

    sc = StandardScaler().fit(Xtr)
    lin = LinearRegression().fit(sc.transform(Xtr), ytr)
    gbm = GradientBoostingRegressor(n_estimators=200, max_depth=2,
                                    learning_rate=0.05, random_state=0).fit(Xtr, ytr)
    span = y.max() - y.min()
    for name, pred in [("Linear", lin.predict(sc.transform(Xte))),
                       ("GBM", gbm.predict(Xte))]:
        print(f"[모델 {name:7s}] test R²(FIT)={r2_score(yte,pred):.3f}  "
              f"MAE={mean_absolute_error(yte,pred):.1f}  (스팬의 {100*mean_absolute_error(yte,pred)/span:.1f}%)")
    print(f"[베이스라인 피드단독] test R²={r2_feed:.3f}  "
          f"steam/feed비 중앙값={(ops[TARGET]/ops['feed']).median():.3f}")

    print("\n[피처 중요도]")
    coef = pd.Series(lin.coef_, index=FEATURES)      # 표준화 → 상대중요도
    imp = pd.Series(gbm.feature_importances_, index=FEATURES)
    tbl = pd.DataFrame({"lin_std계수": coef.round(1),
                        "GBM중요도": imp.round(3)}).sort_values("GBM중요도", ascending=False)
    print(tbl.to_string())
    return ops, gbm, Xte, yte, gbm.predict(Xte), imp


def plots(hb, ops, yte, pred, imp):
    fig, ax = plt.subplots(1, 4, figsize=(22, 5))
    ax[0].scatter(hb["op"], hb["flow"], s=20, c="k", label="mean")
    ax[0].plot(hb["op"], hb["flow_up"], "b.-", ms=4, label="OP rising")
    ax[0].plot(hb["op"], hb["flow_dn"], "r.-", ms=4, label="OP falling")
    ax[0].set_xlabel("steam OP %"); ax[0].set_ylabel("steam flow FIQ-6115")
    ax[0].set_title("Valve char (hysteresis=stiction)"); ax[0].legend()
    ax[1].scatter(ops["feed"], ops[TARGET], s=10, alpha=.5)
    ax[1].set_xlabel("feed FICQ-6101"); ax[1].set_ylabel("steam flow")
    ax[1].set_title("steam vs feed (operating points)")
    ax[2].scatter(yte, pred, s=12, alpha=.5)
    lim = [min(yte.min(), pred.min()), max(yte.max(), pred.max())]
    ax[2].plot(lim, lim, "r--"); ax[2].set_xlabel("actual steam flow")
    ax[2].set_ylabel("predicted (GBM)"); ax[2].set_title("Predicted vs Actual (test ops)")
    imp.sort_values().plot.barh(ax=ax[3]); ax[3].set_title("GBM feature importance")
    fig.tight_layout(); fig.savefig(BASE + "c6111_prodmap.png", dpi=95)
    print(f"\n플롯 저장: {BASE}c6111_prodmap.png")


def main():
    df = load()
    print(f"PROD 정합데이터 {len(df)}행")
    hb, a = valve_char(df)
    ops, gbm, Xte, yte, pred, imp = regress(df)
    plots(hb, ops, yte, pred, imp)


if __name__ == "__main__":
    main()
